Class 10000 Clean Room Project Case
As following is a Class 10000 Clean Room project case display. It is a Class 10000 clean room for a food factory.
Air exchange times：≥20 times/hour
The pressure difference between the main workshop and the adjacent room： 10~15Pa
Air flow: non-unidirectional flow
Temperature: in Winter≥16℃; in summer≤25℃
New supplementary air volume：20%~30% of the total air volume
1. The glass on the outside wall of the clean room is vacuum double-layer glass. And in the internal compartment is single-layer glass. The wall,ceiling and door inner door panel is magnesium sandwich panel. This type sandwich panel has excellent fire-resistance(A1 level).
2. From non-clean room to clean room, goods and worker pass need pass through the air shower room. In the interior of the clean room, the door is generally the airtight door, and the pass box is used for the delivery of goods.